Combine safety and economic benefits in an extraction system
VAV Extraction System
The system uses constant velocity readings, as soon as it is low, the sensor sends the information to the central controller, which in turn passes the information to the actuator that adjusts the opening of the damper so that the speed returns to the desired levels.
In addition to the clear and obvious safety benefits of this system, the benefits are also economical. Since the extractions and air volumes are always adapted to the existing needs and there are no unnecessary consumptions, also the room HVAC must be a system with variable air volume, this way, we have an optimization of the consumptions, never having unnecessary consumptions.
Although it is a system that allows for day-to-day savings, it is a much more expensive system to purchase than the CAV, however, the savings in use ends up compensating the user a lot. In case of using a VAV system hood also the room HVAC will have to be thought of as VAV, so that room parameters are fulfilled for your own safety.
As the name implies, the VAV system is a system that varies the volume of air extracted depending on the opening of the window, so we have a stable face velocity, this implies that the safety of the user is guaranteed with the window open or closed. The VAV system comes with a speed reader that makes a constant reading of the extraction values and communicates to the central system which in turn gives information to the actuator that opens or closes the damper a bit, thus controlling the extraction volume and speed facial. This is the most advisable system for a laboratory, since it always guarantees the safety of the user and allows a better saving of energy expenses.
For a more automated extraction
As an extra safety measure, when the window aperture exceeds 500mm or when conditions are not ideal for using the fumehood, the interior light goes from pure white to red, thereby alerting users in a very visible way that the fume hood should not be used under the conditions in which it is at that moment.
Industrial Laborum has two types of controllers; the ILI controller which is the base VAV, the cheapest version to buy, but nevertheless not much different in security levels compared to premium systems. The second controller version, are the premium versions, these versions feature systems from the most different renowned brands in extraction systems in the world, they all have approximately the same characteristics, differing only in some aspects in the controller. The choice of VAV system should not only be monetary, as the system will be introduced in the internal HVAC system we must take into account that the brand we are using in the HVAC, and try to make the VAV brand the same, since the compatibility systems will be much higher.
The CAV system is the cheapest at the time of purchase, but in the long run it becomes the most expensive. Since this does not adapt to the opening of the window, the air volume will have to be calculated for the maximum opening, this implies a high volume of extracted air. Thus, the volume of replacement air in the room will be high, as well as the temperature and pressure control in the room will have much higher costs compared to other systems.
The extraction carried out by the hoods with CAV system is an extraction that does not necessarily imply an HVAC in the room, it is also governed by a CAV system, however, an HVAC with VAV system is the most recommended, since the control of the area where the hoods are inserted be as accurate as possible. This also makes it possible for the user to use only a hood without a sudden rise in temperature or an increase in pressure, which could put the user in danger.
All these variants later turn into high laboratory maintenance cost. It can be summarized that the CAV system is not the most suitable for large laboratories, and that despite being cheaper in the short term, in the long term it is the most expensive.
Of all traditional extraction systems, the most recommended is the VAV system. A system that performs constant speed measurements inside the hood, thus being able to adapt the extracted air volume. This adaptation of the system to the conditions allows for substantial energy savings and user safety to be improved, despite being a more expensive system than the CAV.
With a VAV extraction system, it is recommended that the laboratory's HVAC be also a VAV system, since this way the accuracy of pressure, temperature and all environmental parameters in the room are guaranteed and remain so.
The end result of this initial investment, (systems with a higher price), is that user safety is improved and the maintenance cost of the hoods in use is much lower compared to the CAV system. This is the recommended system for large laboratories and for areas where atmospheric pressure and temperature control will have to be precise.
We are available to contact you, as we also develop solutions for areas other than those mentioned above.
Industrial Laborum Ibérica is a company with 43 years of experience in the market, which seeks to bring the quality factor to all laboratories. Through customers in the most diverse areas, such as health, education and different industries, ILI has acquired know-how that is the perfect combination with each need or request of its customers. We are here to develop laboratories for people.